Outlets shall be manufactured with a 6-1/2″ [165 mm] length type “K” , flared to 1/2″ [12 mm] inside diameter, copper inlet pipe stub which is sliver brazed to the outlet body. Body shall be one piece brass construction. For positive pressure gas services, the outlet shall be equipped with a primary and secondary check valve and the secondary check valve shall be rated at a maximum of 200 psi [1,379 kPa] in the event the primary check valve is removed for maintenance. Outlet bodies shall be gas-specific by indexing each gas service to a gas-specific dual pin indexing arrangement on the respective identification module.
A colour coded label shall be used for ease of gas identification and aesthetic appeal.
The latch-valve assembly shall be British Standard type and only accept corresponding British Standard type gasspecific adapters.
All outlets shall be cleaned and degreased for medical gas service, factory assembled and tested.