The medical gas outlet shall be an Amico Alert-1 series.Outlets shall be manufactured with a 7-3/4″ (197 mm) length type K 1/2″ (12.7 mm) outside diameter (3/8″ nominal) size copper inlet pipe stub which is silver brazed to the outlet body. The body shall be of 1-5/16″ (33 mm) diameter, one piece brass construction. For positive pressure gas services, the outlet shall be equipped with a primary and secondary check valve and the secondary check valve shall be rated at a maximum of 200 psi (1,379 kPa) in the event the primary check valve is removed for maintenance. Outlet bodies shall be gas-specific by indexing each gas service to a gas-specific dual pin indexing arrangement on the respective identification module.A large, color coded front plate shall be used for ease of gas identification and aesthetic appeal. With the back rough-in mounted, the outlet shall adjust up to 3/4″ (19 mm) variation in mounting plate thickness.The latch-valve assembly shall be DISS type and only accept corresponding DISS type gas-specific adapters.All M.R.I. outlets are manufactured from nonferrous materials.All outlets shall be cleaned and degreased for medical gas service, factory assembled and tested.The outlets are UL Listed and ETL Listed.Amico products comply with NFPA 99. Amico Medical Gas Outlets, Amico Console Outlets, Amico, Instrumental Air DISS (NFPA) Console Outlet.